Spot 300w/ 400w/500w led industrial light outdoor stadium light high mast industrial lighting
* IP65 Outdoor LED High Bay Lighting series can be widely used in outdoor, outdoor or half indoor lighting, like mechanical or electronic processing workshops, storage warehouses, steel mills, gas stations, toll booth,waiting rooms, the platforms of railway station , indoor stadiums and flower cultivating tents etc.
a. IP 65 rating is designed for challenging environments like water or dust locations.
b. Unique Lens design offers multiple beam angles: 25 degree /60 degree/90 degree
c. High efficiency SMD 3030 chip or CREE XBD, Luminous efficiency: 110-130 lm/w;
d. Meanwell ELG Series led driver,
e. Fast, Flexible Installation , the beam angle can be adjusted to 60 degree and 25 degree, used widely;
Products Technical Specification
LED: SMD3030/CREE XBD
Power Factor: >0.95
Colour Temperature: 3000K, 4000K, 5000K, 6000K (Red/Yellow/Blue/Green availabe)
Input voltage: AC85-265V/AC100-305V
Driver: Meanwell Driver or CE Approval Driver
CRI: >Ra80 ( Customized available, such as CRI>Ra90)
Luminous efficiency: 120-150lm/w
Housing color: Black/ Grey
IP grade : IP65
Beam angle : 25/60/90 degree
Material: Aluminum + PC
Working temperature: -35 °C~ +55 °C
Lifespan: 50000 hours
Warranty: 3-5-7 years
Product Dimension (unit: mm)(400w)
Light Distribution Curve (60 degree)
Product Packaging & Shipping
400w 1pcs/carton, carton size: 53x53x62cm, 15KG/carton
1.In case of fire, explosion, electronic shock, the install, inspect and maintenance must be operated by professional people.
2.Please make sure the power off before operation!Luminaries must be electronic grounding!
3.Please make the voltage supplied is available for the luminaries!
4.Please make the luminaries working under the limited working temperature!
5.In order to guarantee enough air convection, luminaries should not be installed in narrow space!
1.Cut off power before maintenance
2.Clean the LED bay light regular to keep good light transmission.
3.Clean the dusk on the surface and heatsink regular to keep good heat dissipation.
4.Do not use water or strong corrosive liquid to clean the lamp, dry cloth is better.
5.Replace LED driver: use screwdriver to open the cover, fetch out the driver. You can see three AC wires, Match brown wire with “L”, Blue with “N”,
Kelly or yellow with “G”. The red or white wire on driver is the positive electrode, black wire is the negative electrode.
Notice, pls confirm the positive and negative electrode has not met extremely instead